Guangdong, China (Mainland), FOSHAN,China (Mainland)
ISO9001,8060 hours certificate;CE
smooth and tidy
Standard or Nonstandard:
1000000 Piece/Pieces per Day 10000000 pieces per week
Packaging & Delivery
Sockets are packed in small box and then in carton with three boxex
For two weeks
Best Pvc Pipe Fittings/110mm Pvc P trap for drainage system
Descriptions Of Our Products:
Pipelines for water supply and drain ,Female and male Coupling ,Socket, Cap , Tee , Adapter , Elbow , Reducer, Union , Plug , Pipe Clip , Valve
white colour for PVC products
at least 50 years
specification is as follows:
Carton Size (mm)
1. Good aging resistance with normal lifetime up to 50 years;
2. Purified water, drinking water system;
3. Solar heating and cooling equipment system;4 4. Beverage and liquid medicine production system; 5. Industrial compressed air pipe network;
6. Caliduct, floor and wall heating equipment;
7. Indoor and outdoor pipe of exposed installation;
8.Oxygen pipe in hospital;
9. Other industrial and agricultural pipe.
4.Jointing of PVC-U Drainage Pipe fittings
A. The following procedures should be adhered when making socket-spigot jointing: 1) Clean the external surface of spigot and internal surface of socket before jointing. 2) Measure the depth of socket, and make the spigot at the distance equivalent to the depth of the socket. 3) Apply solvent cement, first spread to the internal surface of the socket, then to the pipe end evenly and in adequate quantity. 4) Push the pipe into the socket till reaching the mark, and then rotate it by 90°. 5) Remove all excess solvent cement around the joint. 6) The joint should be left undisturbed until it becomes solid.
B. Cautions on the use of solvent cement: 1) Unpacked solvent cement and cleaning fluid should be used immediately and only by designated people. 2) There should be no flame near joint, and ensure adequate ventilation. 3) Bonding should not take place under -10°, and the joint should not be warmed by fire.
5.Application of PVC-U Drainage Pipe fittings
1. Internal and external discharge piping are widely used for industrial and civil high building; 2. The continuous sewerage discharge temperature should not exceed 40°C, and the instantaneous sewerage discharge temperature should not exceed 80°C;
6.Cutting and Chamfering of PVC-U Drainage Pipe fittings
1. Cutting: ---The cutting length should be determined by measurement and according to the dimensions of fittings; ---Use fine tooth panel saw, cutter and pipe cutting machine; ---The cut should be square without any distortion; 2. Chamfering: ---The outside edge of the pipe end should be chamfered to 15°-30°using medium grade file; ---The chamfer length is generally not less than 3mm, and the chamfer thickness is 1/3-1/3 of wall thickness; ---Remove scrap after chamfering.
7.Protection of Socket and Spigot
---After jointing, remove excess adhesive by using cleaning agent such as acetone; ---Wait till the bond cure according to the adhesive behavior and the circumstance condition; ---In winter, the cure time should be adequately prolonged.